All forced air furnaces use a ducting system to distribute the warm air throughout the house. Such ducting should be cleaned out by a professional duct vacuuming service every five years, watch our for the lower quality cleaning services, they are a waste of time and $.
Older duct systems may contain some asbestos tape around the duct joints and in some instances, at the registers or lining of the ducts themselves. Such asbestos containing material, if it is in good condition, is best left alone. Any deteriorated material should be removed professionally and replaced with a water-based mastic.
Many newer homes use flexible ducting which has the advantage of a relatively easy installation and good insulation. However, such ducting can separate from the registers or the furnace when poorly installed, resulting in poor heat distribution and poor furnace efficiency.
|A word (or two) about Heating Ducts from the experts at Ecotope:|
In the past decade, ducts in residential forced-air distribution systems have been recognized as significant sources of wasted energy. As a result, there is growing interest in the efficiency of duct systems on the part of utilities, weatherization programs, building code regulators, and others. Several studies have quantified the magnitude of these losses in small samples of buildings around the United States.
A study by Ecotope conducted in the early 1990s found that 22 homes with at least 50% of the ducts in unconditioned spaces (crawl spaces and garages) averaged about a 29% efficiency loss due to leakage and conduction losses, compared to about 2% efficiency loss in two homes with all interior ducts. Air sealing retrofits on six of these homes which were selected to have a large amount of leakage to outside ("outside" being the crawl space or garage), resulted in an improvement of the efficiency of about 16%. Other studies have found similar results.
Duct losses are due primarily to air leakage and conduction losses. These losses interact in a complex manner, with leakage and conduction losses interacting with each other, and with return and supply losses influencing each other. Other factors that influence the amount of additional energy consumed to condition the home are regain and the interaction of duct leakage with overall home air leakage. Regain is the change in losses from the conditioned space to unconditioned spaces due to a change in the temperatures of the unconditioned spaces due to duct losses. Reg